Program affected: PIPE-FLO Professional 12
Approved by: JLS
Build numbers affected: 12.0.19520
In PIPE-FLO Professional 12, if there are duplicate entries on the Installed Valve & Fitting List for a Pipe (same number and type of V&F), only one entry is reported to the DataLink Fittings Data Table. This does not effects the accuracy of any calculations in PIPE-FLO, but does show up as a discrepancy in the list of installed valves and fittings in the Pipeline Report and Bill of Materials Report, as well as the list if extracted using DataLink.
- The user adds duplicate entries to the installed valves or fittings list for a pipe.
(for example “1 x Butterfly” and “1 x Butterfly”)
- User generates a Pipeline Report or Bill of Materials Report
- The report displays only “1 x Butterfly” in the list of installed valves and fittings.
Add identical valves and fittings as a group rather than adding them to the pipeline individually. (ie: "2 x Butterfly" rather than two single valves).